|Skip Navigation Links|
|Exit Print View|
|Sun Server X2-8 (formerly Sun Fire X4800 M2) Rackmounting Hardware Installation Guide Sun Server X2-8 (formerly Sun Fire X4800 M2) Documentation Library|
The rack mounting hardware is compatible with a wide range of equipment racks that meet the following standards:
Four-post rack (mounting at both front and rear).
Note - Two-post racks are not compatible.
Rack must have 5RU space available.
Rack should have a horizontal opening and unit vertical pitch conforming to ANSI/EIA 310-D-1992 or IEC 60927 standards.
Distance between front and rear mounting planes between approximately 26 and 34.5 inches (660.4 mm and 876.3 mm).
Minimum clearance depth (to front cabinet door) in front of front rack mounting plane: 1 inch (25.4 mm).
Minimum clearance depth (to rear cabinet door) behind front rack mounting plane: 27.5 inches (700 mm).
Minimum clearance width (between structural supports and cable troughs) between front and rear mounting planes: 18 inches (456 mm).