Note - Proper airflow into and out of the server is essential for keeping the server's internal temperatures within a safe operating range.
The server draws cool air from the front of the server and expels hot air out the rear. To avoid overheating the server:
Ensure that inlet air enters at the front of the server and exits from the back.
Do not direct warm air toward the front air intake of the server.
Prevent recirculation of exhaust air within a rack or cabinet.
Manage cables to minimize interfering with the server exhaust vent.
Ensure that the server ventilation openings used for intake and outflow of air provide an open area that is at least 60% of the open area perforations across the front and rear of the server.
Allow a minimum of 0.2 in. (5 mm) clearance at the front of the system and 3.1 in. (80 mm) at the rear of the server when mounted. These clearance values are based on the preceding inlet and exhaust impedance (available open area) and assume a uniform distribution of the open area across the inlet and exhaust areas. Clearance values greater than these are recommended for improved cooling performance.
Note - Be mindful that the combination of inlet and exhaust restrictions, such as cabinet doors and the spacing of the server from the doors, can affect the cooling performance of the server.